CJ1W-PRM21 Omron Automation and Safety Controllers CJ1 Profibus Master datasheet, inventory, & pricing. This article (NJ base) explains how to setup the configuration for the NJ with a CJ1W-PRM21 Profibus communication unit connecting. Buy Omron CJ1W Series PLC I/O Module, 31 x 90 x 68 mm CJ1W-PRM Browse our latest plc-i-o-modules offers. Free Next Day Delivery.
||11 November 2015
|PDF File Size:
|ePub File Size:
||Free* [*Free Regsitration Required]
Hope this helps, Daniel Chartier. Posted 21 March edited. I configured in S7 project the slave parameters.
But still I can’t scan in order to find connected slaves. Started by malyalewariat18 March prm21 cj1w bus profibus. Hello, the BF led blink in the omron master, the slave appear only with the led run. I’ve made mistake, because communication module is diffirent than I mentioned before.
The module was update to firmware V3, but I have only in step 7 the product versions 1 and 2. Site Explorer Site Explorer.
Have a look at the following FAQ and attached links: When I use “Test” option or just go online I get errors: It supposed to be toolbus usb in configuration tab, and now i can use test, and go online options without any errors.
When i try to use scan option i get another error: What about those errors? I was sure that I’ve tried all but I didn’t. I have no idea. If this is already done, it would be good to see how they have been configured.
What I can do. All about Decentral Peripherie. Seeing the scan returns error with DTM version 1. Create an account or sign in to comment You need to be cjj1w member in order to leave a comment Create an account Sign up for a new account in our community.
Am Cjw missing CX-Server? In the front of the module apeare that is the version 2. Following DTM reported the error: I’ve set up correct connection parameters of cj1w-prm profibus master.
myOMRON Europe: Services & Support
I’m almost sure that this bosch unit provides profibus connection. Share this post Link to post Share on other sites. Follow us on Twitter Youtube.
Product Support Services Forum mySupport. Edited 21 March by malyalewariat. Hello Daniel, Thanks for your answer. It is profibus slave. I should do any thing else, Thaks. Hello Ariel; In your diagnostic messages a few stand out, at first glance ArielP 10!!
You need to be a member in order to leave a comment. When i try to use scan option i get another error:. Here I have que diagnostic of the cp slave. This contribution was helpful to 1 thankful Users dchartier. The number of bytes its going to recive and send.
So many communication protocols to choose. Register a new account. Sign in Already have an account? I made a diagnostic to de cp and appear this error: I can now pprm21 diagnostic option and I can see states of plc and module.
Sign up for a new account in our community. Ck1w master tell me that the slave have a invalid response. Started by malyalewariat18 March. But it’s possible that the problem is the hardware config. The GSD file you will find here: Sign In Sign Up. Try to run the AutoUpdate so you’ll get a newer version if you have a registered copy. I don’t have this software installed on pc